AC Repair Oldsmar
Oldsmar best AC repair service
When the temperature raises sky-high, we seek comfort in our home, where an efficient cooling system can keep us cool. But if you need air conditioner service, what will you do for AC service Oldsmar, FL?
For air conditioning repair reach out to Hot 2 Cold and then, a professional air conditioner service technician will be on the way. We’re unlike other Oldsmar air conditioning repair companies, who charge high fees just to show up and then end up saying you need a new system. Call for AC service Oldsmar, FL for quick troubleshooting and repair advice
Repair or replace your air conditioning system.
Hot 2 Cold is Oldsmar’s area top rated service and repair provider. Our service technicians are true techs on salary non commission employees who will not upsell but provide options on repair, service or maintenance options. $79 or $1(for maintenance club customers) service is included with repair. Under the circumstance that the unit is not repairable and a quote for a new HVAC system is necessary-the service tech will have a comfort advisor come out to take over and to explain new installation options and guide you through that process. (Our techs provide repairs not quotes)
Virtual Troubleshooting for Oldsmar Air Conditioning
- Hot 2 Cold offers a free and virtual air conditioner service call.
- This proves to be helpful for DIY customers who need air conditioning repair.
- Phone Troubleshooting may save the need for a service call when you need an air conditioner repair Oldsmar FL.
Contact us for Air Conditioning Repair for these Oldsmar HVAC issues
- When AC crashes suddenly
- When the outside unit is not functional
- Issue with the airflow or frozen coil
- AC doesn’t cool enough
- A clogged drain line
- To repair refrigerant leak
- No air conditioning in all locations
- Annual maintenance
If you’re looking for a reliable Oldsmar air conditioning repair company/contractor then call Hot 2 Cold and get quality assistance on the same day of your call. Please call Hot 2 Cold and get timely air conditioner repair Oldsmar FL services.
Oldsmar, FL Zip Codes: 34677, 34685
for Oldsmar, FL
Review for James
Jerry - Oldsmar, FL 34677
Drain line bill out
Today we visited for the downstairs AC unit again. This machine has been intermittently shutting down at unscheduled times. We learned the issue was a malfunctioning float switch/water sensor. The sensor was removed today to prevent false system trips. The switch will be replaced during the next planned filter replacement.
Today we visited because the downstairs AC unit thermostat kept going blank. We learned the condensate drain line was backing up. While on the roof we cleaned all three drains. The systems are on and working well.
Today James visited to evaluate the warm conference room. To better cool the conference room we dampened some air from the front offices to direct into the warm space. The ceiling diffusers were manipulated to allow more airflow. James will be in touch with Maireni for feedback and next steps.
Found no issues with the system both compressors and blower are working thermostat was set to 72 reading 72 system up and running
Today we visited to determine why the thermostat went blank. We learned the unit had a clogged drain line. After cleaning the drain the system performed as it should.
Today we visited because the AC was not working. The drain line was backed up and this triggered the float switch and turned the unit off. If this issue continues we should consider eliminating the p-trap at the air handler because the unit has a trap where the drain goes under the building foundation.
The Bosch IDS Light is the first 15-SEER Inverter condenser on the market. This BOVA15 outdoor system combines the standard efficiency with our BVA15 fixed-speed air handler. With IDS Light, you get the benefits of our inverter system at a price point you’ll love!
Repair Option Repaire leak inside condenser recharge system with 7lbs of 410a replaced the defrost board and filter drier bi flow Future repairs are electrical disconnect has been bypass must be replaced also compressor call office for cost
Found system out of refrigerant,gave estimate for new evaporator coil filter drier and refrigerant, $2790.00
Relocated white wire from w2 to w on thermostat for existing carrier equipment and climbed up on roof to verify proper operation
Talk with customer need to reschedule first thing in the morning they close at five