When the temperature raises sky-high, we seek comfort in our home, where an efficient cooling system can keep us cool. But if you need air conditioner service, what will you do for AC service Riverview, FL?
For air conditioning repair reach out to Hot 2 Cold and then, a professional air conditioner service technician will be on the way. We’re unlike other Riverview air conditioning repair companies, who charge high fees just to show up and then end up saying you need a new system. Call for AC service Riverview, FL for quick troubleshooting and repair advice.
Virtual Troubleshooting for Riverview Air Conditioning
- Hot 2 Cold offers a free and virtual air conditioner service call.
- This proves to be helpful for DIY customers who need air conditioning repair.
- Phone Troubleshooting may save the need for a service call when you need an air conditioner repair Riverview FL.
Contact us for Air Conditioning Repair for these Riverview HVAC issues
- When AC crashes suddenly
- When the outside unit is not functional
- Issue with the airflow or frozen coil
- AC doesn’t cool enough
- A clogged drain line
- To repair refrigerant leak
- No air conditioning in all locations
- Annual maintenance
If you’re looking for a reliable Riverview air conditioning repair company/contractor then call Hot 2 Cold and get quality assistance on the same day of your call. Please call Hot 2 Cold and get timely air conditioner repair Riverview FL services.
Riverview, FL Zip Codes: 33568, 33569, 33578
for Riverview, Brandon, Valrico, Apollo Beach, Sun City Center, Ruskin, FL
Diane - Valrico, FL
Prices are high
James - Valrico, FL
Good try. But price was too high.
Robbie - Apollo Beach, FL
Technician was great, tried to resolve. Was unfortunately unable due to condition of our equipment. Quote to replace was the highest of 3 quotes.
Great company to work with, highly recommend!!
Chris - Brandon, FL
Very impressed with both James’s knowledge and helpful nature! He was a pleasure to work with ❤️. The guys that came to do the work were very respectful of my property, cleaned up before they left, and I very much appreciated their hard work.
Jennifer - Apollo Beach, FL
Luis and Hector were great had our new unit in the next day
Great service! Great tech!
Britton - Riverview, FL
Geraldo was great! He fixed our air and was friendly, kind and professional. Ten out of ten
Roy - Riverview, FL
Dennis - Riverview, FL
The service tech really knew what he was doing.
Anahi Aguilar - Riverview, FL
Was very happy that he knew little Spanish and understand the situation and broke it down for my mother to understand
Quick and Efficient
Ashley - Riverview, FL
Perform diagnostic and evaluation of System operation and present Customer with multiple options for Maintenance, Repair, or Replacement of System. Found system to be r22 without any Freon in the system quoted homeowner for anew system
1 Time Maintenance and Club Membership Santi duct blower ok drain line flushed comp ok fan ok charge ok cap ok system up and running
Drain line was clogged. Rinsed down primary drain line. System operation normal.
He says only at particular times throughout the day it sounds like ufos in his attic above the air handler closet in the bathroom. Disconnected normally open zone dampers to see if this sound may have to do with the zoning. The homeowner suggested he would rather his system not be zoned. Need to return and spray glue tape and mastic side of unit were there is air leakage
Found leak in 3/8 copper in attic repaired and recharged system
Perform diagnostic and evaluation of System operation and present Customer with multiple options for Maintenance, Repair, or Replacement of System. Customer will pay online
Replaced bad 40/5 uf run capacitor. Refrigerant checks ok. Evaporator coils are very impacted and require pull and clean. System takes a 20 x 20 x 1 air filter
Perform diagnostic and evaluation of System operation and present Customer with multiple options for Maintenance, Repair, or Replacement of System. Upon arrival customer already cleared drain Made sure unit was operational
Today we visited to provide pricing to replace the AC unit and determine why the current system has been problematic. We learned the existing machine is undersized, the ductwork is inadequate, and the refrigerant lines are not correct. James put together the available options and emailed them to Christie and Jim.
Perform diagnostic and evaluation of System operation and present Customer with multiple options for Maintenance, Repair, or Replacement of System. Find evaporator coils are partially impacted. Recommend a pull and clean for optimum performance. Blower wheel is in clean condition. On outdoor condenser there is a half inch seal tight fitting for high voltage that needs reducing washers so that wiring does not vibrate against sharp metal and cause hazard. Refrigerant levels are good. Amp draws are good.