Corey and his crew did a great job installing our new system.
Great service and helpful tips!
St. Petersburg, FL
He was quick and great!
John was very professional and polite, diagnosed the issue immediately and fixed it. Price was fair, John was friendly and in & out in no time
Great customer service
Sean from Hot 2 Cold recently sealed our attic AC and replaced our filter. He was on time, thorough and did an excellent job! Thanks, Sean!
Convenient High Quality Service
Apollo Beach, FL
Pretty fast explained well
Hector was right on time for our system check-up. He was very thorough in explaining everything he was measuring and testing. Gave us some tips on self maintenance and what we could do to keep system running great. I give him five stars!
Dade City, FL
Michael showed up on time and did the job, he was courteous, friendly and cleaned up when finished.
Terrific service.. prompt, friendly and explained everything in detail .
Great service, very professional.
Great job, always the best people work at hot to cold.
I have to say every time I call this company they sent experience technicians fast and very professionals. On this particular case, technician John Campbell came over and troubleshooted my problem fast, it was a bad capacitor changed and installed a new one fast and everything came back to normal fast. Thanks to John Campbell and Hot2Cold to make it happen!
Replacement of the faulty thermostat with a basic non-programmable thermostat.
This is the most basic equipment available for purchase today. It uses a single speed compressor and a single speed indoor fan. This unit is the least expensive to initially purchase and install.
Filter was heavily impacted. Filter type being used even when clean greatly reduces air flow. Recommend installing a media filter package in the garage. Recommend hard start kit to avoid premature compressor failure from difficult start ups due to problematic airflow issues. Clean filter is so restrictive temperature split was 30 degrees. Refrigerant check ok. Recommend preventative maintenance be done over entire system.
Today we learned the system was not working because of a faulty thermostat. James, the first technician, did not have the correct thermostat for the repair. Sean will be returning to complete the repair. Whenever James left, he left the thermostat wires nutted together so the hole would cool down.
PERFORMED ROUTINE MAINTENANCE. INSPECTED ALL ELECTRICAL AND MECHANICAL PARTS, INCLUDING AMPS, VOLTAGE, CAPACITOR, FLOAT SWITCH, CLEANED COILS WITH FOAM CLEANER, CLEANED AND VACUUMED OUT DRAIN LINE. EVERYTHING WORKING GOOD AT THIS TIME.ðŸ˜Ž
Upon arrival found unit and ductwork completely saturated After further diagnostics we learned that the P-trap in the attic was not set up properly and not allowing the system to drain correctly. Eliminated p-trap and designed one at the end of the drain line outside system functioning properly at this time and draining properly
UPON ARRIVING FOUND BLOWN OUT DUAL RUN CAPACITOR 35/5, AFTER REPLACING EVERYTHING IS WORKING GOOD AT THIS TIME.ðŸ˜Ž DUAL RUN CAPACITOR 35/5
UPON ARRIVING FOUND SYSTEM LOW ON 410-A REFRIGERANT, AFTER INFORMING CUSTOMER I ADDED 2 LBS. OF 410-A.
James put together the repair and replacement pricing for Werner.
Installed trap in primary drain line
Upon arrival system was in the cool mode but not running. We learned that the indoor fan motor is bad and needs to be replaced As well as the outdoor fan motor is bad and needs to be replaced
Upon arrival we learned that the drain was unlevel causing it to back flow and over flow the drain pan in the air handler. The safety switch for the drain was left resting up above the drain level so the unit kept running. Also unit needs a maintenance done. Writing estimates for customer Redesigned drain line to where the down spout through the wall is at a lower level than before
Washed evaporator coils with self rinse solution. Washed down condenser coils and primary drain line. Amp draws across motors are normal. 20 degree temperature differential across evaporator coils. Subcool and superheat are in range. Media filter needs to be changed. 20 x 20 x 4.5 filter is pretty impacted. Suggest replacing filter twice a year.
Today we visited to
CUSTOMER CHANGED HER PHONE NUMBER, AND FORGOT TO CALL, TO LET US KNOW THAT SHE NO LONGER REQUIRED OUR SERVICES...
Today we discovered the upstairs system not working due to a failed defrost control board. I was able to get the unit running by bypassing the control board. The unit is running at the moment, but all of the sensors are bypassed. So, the unit will be okay for a little while unless there is another problem with the system. If we leave the unit in this condition it can damage itself should another part fail.