Great Service prompt and knowledgeable, very reasonably priced.
excellent customer service
Easy Going and Informed
James was great. Felt super comfortable with him being an ME. Got us on the schedule to do the work pretty quickly, too.
Great Customer Service
John is an excellent and informative technician. He explains the process in details and ensure you understands your options and/or answers all questions and concerns.
Price Quoted Was 38% Above the Competition
1. Price quoted was 38% above what I later paid your competitor for the EXACT same products and services. 2. Technician called me "Different" because I chose not to have him perform the proposed work on my systems. 3. It was inconvenient to schedule a competitor after your technician departed my home. 4. I do not plan to use your company's products or services in the future.
Tarpon Springs, FL
As always, Hot2Cold service personnel are great
Relay circuit board issue
Did what needed to be done and did so cheerfully!
one word SUPER
Couldn't had asked for any better service.
Luis Taipe Tello
Great service and quick resolution of the problem
Hot 2 Cold continues to impress! They respond quickly and resolve the issues in a timely manner. Best ac company in Tampa.
Very professional, super nice and knowledgeable and always reliable. Highly recommend Hot 2 Cold.
Awesome Company with Great Service!
Mark C. -
I will recommend HOT2COLD to everyone in need of AC repair or replacement. Excellent service from the Techs to Sales to the Installers! A big THANK YOU to the install team lead by Corey B. for my new unit. They were exceptional!
Very pleased with the outcome from the service. Mr Campbell was very professional and very helpful.
Great service, super friendly and knowledgeable.
5 stars. Highly recommend this company for all AC work and maintenance.
Professional, personable and expertise
Tech was Hector and without a doubt his technical expertise as well as his professional and personal demeanor is nothing short of beyond comparable!!! I called this morning in hopes of receiving some help and within maybe an hour Hector was calling me to inform of his time of arrival.. TALK ABOUT CONVENIENCE!!!!
Very satisfactory service
Had an ongoing problem with the air conditioning unit was completely and efficiently resolved.
Found system cooling with 76degrees in house,customer says system running all the time,and wonâ€™t get temperatures down any lower during the hot part of day. 784sf mobile home,made minor adjustment in charge,cleaned coils and drain,system checked good and draining properly.
Verified proper float switch operation. Explained proper filter maintenance as it pertains to ice overs and installed a t in primary drain line for downstairs system.
Found AC filter completely clogged,removed filter and shut system down to defrost.customer will call to schedule maintenance.
Today we reset the unit and thermostat. I made the thermostat and unit think it had just been installed so that all of the algorithms, airflow, and preferences could be restored. Once everything was reset the system came on and cycled properly. Ron will let me know how things go.
Completed Free Annual Maintenance Blower and coils are clean Primary drain line is clear Filter was severely impacted replaced with 3M filter that homeowner had in closet Electrical components are good Compressor amp load is normal Temp Differential is 19 degrees Humidity is 54% Tstat set to and reading 72 Degrees Per homeowners request increased overcool to 3 degrees Pressures are normal System operation is normal at this time Need to order Aprilaire filter for homeowner Free 1 Time Maintenance
Dropped off one jug R410A
Picked up 3 jugs R410A
Clogged drain. Drips pan full of water. System working normally
Added 5 lbs. refrigerant r410a
Clogged drain, maintenance clean condenser clean drain line.
DUAL RUN CAPACITOR 30/5 AND 2 LBS. OF 410A REFRIGERANT
Found blower not coming on and wireingAt terminal Board inside air handler very corroded and not making good connections,also 60 amp disconnect breaker will not come on. Installed new blower motor,cleaned assembly and bypassed terminal board to correct corroded wireing,and installed new 60 amp breaker of customers.system checked good and draining properly.signed customer up for maintenance. Customer will pay online.
UPON ARRIVING FOUND DRAIN PAN FULL. CLEANED AND VACUUMED OUT DRAIN LINE AND DRAIN PAN. ALSO 45 TO DRAIN LINE. SO AIR WOULD NOT SUCK BACK IN. EVERYTHING WORKING GOOD AT THIS TIME. ðŸ˜Ž
Picked up motor $670.03 inv#1309237
FOUND LEAK AT AIR HANDLER ON LINE SET, PERFORMED REPAIR, VACUUMED DOWN TO 270 MICRONS AND FILLED TO SPECS, USING COOL CLOUD APP. TESTED OUT
Variable speed blower motor, blower clean, and preventative maintenance
Found leak in evaporator coil,condenser is on roof,5 stories high,could not confirm leak in condenser coil.
Clogged drain, drip pan full of water. System working normally.
Found system reading lock rotor code on board,condenser not running.reset board and system started and running properly,adjusted sub cooling and installed hard start kit.temperatures and pressures checked good and draining properly.
UPON ARRIVING FOUND BAD DUAL RUN CAPACITOR 30/5 WITH WITH LIZARD LAYING ACROSS AFTER CHANGING, EVERYTHING WORKING GOOD AT THIS TIME.ðŸ˜Ž. TESTED OUT