Do you need Air Conditioning or HVAC Repair in Tampa?
Yes! Well, the solution is to give Hot 2 Cold a call. An experienced AC or HVAC technician is available to answer you questions. We have a professional team providing complete HVAC and AC solutions for air conditioning in Tampa.
Hot 2 Cold’s HVAC technicians take pride in presenting you with all options to repair and service your air conditioner or heat pump. The technician will visit to check the HVAC unit to determine the technical problem and then will suggest the best solution to repair it.
- Reliable HVAC and AC repair and replacement services
- Air Conditioner Repair services by professional technicians
- Prompt customer care helpline; many have HVAC and AC knowledge
- AC repair services at appropriate costs
We offer assistance for any of the problems your Air Conditioning System has:
- Sudden crash or failure
- Non-functional outside unit
- Problem of frozen coil or improper functioning with little airflow
- If the unit does not cool enough or keep up with the Tampa Bay heat
- No air conditioning in all rooms
- Fixing clogged HVAC drain line
- Repairing HVAC refrigerant leaks
- Annual AC maintenance
So, whether AC unit crashes, or outside unit is not functional, or an annual maintenance is needed! Contact us for the best solution and service in Tampa.
Click to CALL (813) 580-8006
for Tampa,lutz,thonotosassa,cheval,citrus park,, FL
John - Tampa, FL
Stephanie - Tampa, FL
Jason was absolutely the best man for the job. He was informative and very knowledgeable. We at FedData are very pleased with selecting Hot2Cold as our service provider and we look forward to an excellent working relationship.
What professionalism looks like
Chris - Tampa, FL
Hot2Cold is an excellent experience. James took the time to educate me on what the issues were and offered a range of solutions.
Janus - Tampa, FL
James and Sean did a great job!
Jeff - Tampa, FL
James relentlessly researched options for our out of date wine cellar unit until he found a solution that would work. Sean did a great job with the installation.
Brent - Lutz, FL
More Problems to Fix one
Bret - Tampa, FL
Corey was nice. The team was respectful. I feel like they moved too slow initially to get the work done, then when a installation problem arose, the office was closed. I feel like they created another problem with my condenser (which was working fine). They were asked the move the air handler, and spent a lot of time messing with the condenser outside. Then, they left me with no sore saying the condenser had a problem. I feel like they created the problem and because they didn’t work diligently at the beginning of the project, they had to leave me with 0 air. I still have no air and I’m becoming more and more upset the hotter it gets.
Bleuacier - Tampa, FL
excellent customer service
Ronald - Tampa, FL
Easy Going and Informed
Bret - Tampa, FL
James was great. Felt super comfortable with him being an ME. Got us on the schedule to do the work pretty quickly, too.
1 Time Maintenance sanitized ducts. Sprayed evaporator with self rinse coil cleaner. Washed primary drain line. Hosed off condenser coils and took amp draws. Insulation in air handler was falling and blocking partial blower assembly. Realigned metal rods holding insulation in place freeing blower area. Refrigerant levels are good.
Perform diagnostic and evaluation of System operation and present Customer with multiple options for Maintenance, Repair, or Replacement of System. COMPLETED,Customer has wrong vent in bedroom directing air side to side,needs vent to direct air across room to remove heat load.added two lbs refrigerant for proper charge and humidity removal,cleared drain,system checked good and draining properly.maintenance will change vent and maintenance man approved and signed bill
Today we visited with Gary to provide a plan and pricing to update the air conditioning in his new home. The home currently uses two AC units. Both units are in poor condition while one is not operational at all. The units use R-22 refrigerant and suffer from corrosion. The ductwork in the home is fiberboard ductwork and it too is severely dilapidated. In addition to a few decades of wear the ductwork has rodent damage and feces throughout. James provided Gary with four options to proceed. All four options include once central HVAC unit and a redesigned duct system with a tri-zone zoning setup. Gary currently has a roof project and flooring project underway and stated he will follow up with the questions that come up.
On arrival found compressor not running with t stat calling for cooling. Found bad high pressure switch cutting low voltage to contactor. Bypassed pressure switch and tested system, pressures look good with no reason for high pressure switch to trip. System now cooling but gave replacement options due to age of system being over 10 years old.
New arrival tenant showed me a video of water running out of return in living room. Return is directly below air handler on second floor. Checked both drain lines and neither is clogged. Both Evaporator coils are slanted style coil, coils are very rusty and in poor condition. Water is dripping off of coil instead of running down to the drain pan. Tenant stated they have had many issues with air handlers leaking water and keeping temperature upstairs. Tenant has to run a dehumidifier to control humidity. Emailed estimates for coil replacement but new coils will be slant coils which often have this issue. Also gave estimate to replace both systems with 14 seer that has a frame coils and 16 seer 2 stage equipment for proper humidity control.