When the temperature raises sky-high, we seek comfort in our home, where an efficient cooling system can keep us cool. But if you need air conditioner service, what will you do for AC service Riverview, FL?
For air conditioning repair reach out to Hot 2 Cold and then, a professional air conditioner service technician will be on the way. We’re unlike other Riverview air conditioning repair companies, who charge high fees just to show up and then end up saying you need a new system. Call for AC service Riverview, FL for quick troubleshooting and repair advice.
Virtual Troubleshooting for Riverview Air Conditioning
- Hot 2 Cold offers a free and virtual air conditioner service call.
- This proves to be helpful for DIY customers who need air conditioning repair.
- Phone Troubleshooting may save the need for a service call when you need an air conditioner repair Riverview FL.
Contact us for Air Conditioning Repair for these Riverview HVAC issues
- When AC crashes suddenly
- When the outside unit is not functional
- Issue with the airflow or frozen coil
- AC doesn’t cool enough
- A clogged drain line
- To repair refrigerant leak
- No air conditioning in all locations
- Annual maintenance
If you’re looking for a reliable Riverview air conditioning repair company/contractor then call Hot 2 Cold and get quality assistance on the same day of your call. Please call Hot 2 Cold and get timely air conditioner repair Riverview FL services.
Riverview, FL Zip Codes: 33568, 33569, 33578
for Riverview, Brandon, Valrico, Apollo Beach, Sun City Center, Ruskin, FL
Jon - Riverview, FL
Very satisfied with the service. I will be using them again.
Great tech service. Terrible phone appt
Jeffrey - Valrico, FL
Made appt in line, then called 3 hrs prior to say they would be Kate. Then did not show until after another call
Quick, Fast, Pleasant
Mike - Riverview, FL
My service tech James T. was absolutely amazing. He called ahead of time with his ETA, and started working immediately. He was able to diagnose and fix my issue. I am a new home owner and he was really great with explaining everything and answered all my questions. I will absolutely be calling Hot2Cold for all my HVAC needs
Andy - Riverview, FL
Really nice Techs, very knowledgeable and quick.
Jason - Ruskin, FL
Tony was great. Went over the service with me and his recommendations. Couldn’t ask for a better experience.
Lashawn - Valrico, FL
Tony is an amazing technician. He took the time to educate me and did very thorough work. It was really refreshing to meet someone “these days” that takes so much pride in his work and complete said work with a smile. I will be doing a by name request for him in the future as I trust that he’s honest and cares.
Great Service, Very Knowledgeable
Jackie - Brandon, FL
James was very professional and explained everything that needed to be done in a timely manner.
Great service. Tony is awesome
Curtis - Apollo Beach, FL
William - Riverview, FL
The technician blew my circuit board improperly bypassing it and tried to sell me a new unit. Had another company come out and fix his mess up. They stated he wired it improperly and now my ac is running great.
Technician Tony Lewis
Nicole Alexander - Riverview, FL
Technician Tony Lewis is very professional, proficient, and extremely knowledgeable. We are very impressed!
Repair Option replaced 45/5 uf run cap
System is functioning normal at this time. There are periodic blower communication alerts appearing. I uploaded pictures of the messages to the file. Have Hector to research for the most likely culprit.
1 Time Maintenance performed flushed drainline and checked system operation system up and running at this time
Incomplete- main control board in furnace needs to be replaced. Bypassed evaporator fan motor and turned ac off for two hours so ice formation over coils can thaw. Will need to come back in the morning to check system performance and refrigerant levels and find availability and cost of board. Also vacuumed water out of return
Found blink thermostat and broken red wire in cap replaced the thermstat board was bad t4 installed t6 checked system operation system up and running homeowner going to buy filters
Completed, Performed complete maintenance on two split systems, cleaned coils and flushed drains, checked all electrical heat and cooling temperatures and pressures checked good and draining properly.
COMPLETED Today we visited to determine why the unit wasn’t cooling. We learned the water sensor was tripped because the primary drain pan had sludge built up. After cleaning the pan and drain line the unit came on and is performing properly.
Customer put something in front of the return causing system to freeze up. No charge,customer is waiting 2 months for control board for condenser unit, condenser fan is bypassed and system is cooling good.
Completed, System working,found drain full of something that looked like drier lint, Cleaned drain and system checked good and draining properly.